## think…mercer first^{®}

### Features:

- Designed with "Auto Seat Technology"®
- A low rated and fully guided spring allows for more consistent Set Pressures from pop to pop.
- Consistent Set Pressures allows for repeatable use without the need for excessive repairs or resetting.
- Open, Close, Seat and Seal™
- Fully guided disk for the proper alignment, opening and closing, and reseating of the valve.
- Mechanical Stop prevents wear on parts and controls valve lift.
- Pop Action relief allows the valve to go to full lift at Set Pressure. This helps with DOT regulated applications.
- Non-rising stems allowing valves to be installed in small areas.
- Sour Service Trim available.
- Additional options available to meet NACE MR0175 requirements.
- Canadian Registration Number (CRN)
- Additional options available to meet Conformité Européenne (CE) to PED Directive 2014/68/EU and/or ATEX Directive 2014/34/EU

Orifice | C
(USC) | C
(SI) |
---|---|---|

OrificeStandard Inlet Sizes | C
(USC)¾", 1" | C
(SI)DN 20, DN 25 |

OrificeInlet and Outlet Connection Types | C
(USC)RF x RF, RTJ x RF, RTJ x RTJ | C
(SI)RF x RF, RTJ x RF, RTJ x RTJ |

OrificeActual Orifice Diameter | C
(USC)0.281 in | C
(SI)7.1 mm |

OrificeActual Orifice Area | C
(USC)0.062 in ^{2} | C
(SI)40 mm ^{2} |

OrificePressure Range | C
(USC)15 – 2999 psig | C
(SI)104 – 20677 kPa |

OrificeStandard Temperature Range | C
(USC)-20°F to 400°F | C
(SI)-29°C to 204°C |

OrificeASME Flow Coefficient, K_{d} (Gas) | C
(USC)0.818 | C
(SI)0.818 |

OrificeASME Flow Coefficient, K_{d} (Liquid) | C
(USC)0.707 | C
(SI)0.707 |

*Mercer Valve Co., Inc. reserves the right to change product designs and specifications without notice.*

### 9100 Flanged "C" | Part Number Selection

91 -

17

A

C

B

1

C

1

D

T

E

09

F

C

G

1

H

I

### A | INLET & OUTLET COMBINATION

(

*See*)**Dimensions & Weights**, below.### B | ORIFICE LETTER

**C**– 0.062 in²

### C | INLET & OUTLET TYPE / BODY MATERIAL

**1**

^{★}– RF x RF / WCB CARBON STEEL

**3**

^{★}– RTJ x RF / WCB CARBON STEEL

**2**– RF x RF / CF3M STAINLESS STEEL

**4**– RTJ x RF / CF3M STAINLESS STEEL

**A**– RTJ x RTJ / WCB CARBON STEEL

**B**– RTJ x RTJ / CF3M STAINLESS STEEL

**P**– RF x RF / LCC CARBON STEEL

**Q**– RTJ x RF / LCC CARBON STEEL

### D | CAP TYPE

**1**

^{★}– CLOSED CAP

**2**– OPEN LIFT LEVER

**3**– CLOSED LIFT LEVER

### E | SEAT MATERIAL

**V**

^{★}– FKM

**T**

^{★}– PTFE

**P**

^{★}– VIRGIN PEEK

**B**– BUNA-N

**E**– EPDM

**N**– NEOPRENE

**X**– FFKM

**Y**– VESPEL®

**L**– PC BUNA

**F**– FKM (LOW TEMP)

### F | SPRING CODE

(

*Spring codes assigned by Mercer Valve.*)### G | TRIM CODES

**C**

^{★}– 440C S.S. DISK, 17-4 S.S. NOZZLE (STD GAS SERVICE)

**L**

^{★}– 316 S.S. DISK & NOZZLE (LIQUID SERVICE)

**N**

^{★}– 316 S.S. DISK & NOZZLE (SOUR GAS SERVICE)

**B**

^{★}– 316 S.S. DISK & NOZZLE (SOUR LIQUID SERVICE)

**U**– 316 S.S. DISK & NOZZLE (OPTIONAL GAS SERVICE)

**X**– ALL 316 S.S. (OPTIONAL GAS SERVICE)

**LX**– ALL 316 S.S. (OPTIONAL LIQUID SERVICE)

**BX**– ALL 316 S.S. (OPTIONAL SOUR LIQUID SERVICE)

**NX**– ALL 316 S.S. (OPTIONAL SOUR GAS SERVICE)

### H | O-RING MATERIAL

**1**

^{★}– FKM & BUNA-N (STANDARD)

**2**– FKM 75 DURO

**3**– FKM 90 DURO

**4**– BUNA-N 70 DURO

**5**– BUNA-N 75 DURO (LOW TEMP)

**7**– FFKM

**9**– NEOPRENE

**A**– CHEMRAZ®

**C**– EPDM 80 DURO

**D**– EPDM 90 DURO

**G**– TFE/P

**H**– SILICONE

**J**– FLUOROSILICONE

**K**– HNBR

**L**– PC BUNA

**M**– FKM ED

**P**– FKM 75 DURO (LOW TEMP)

### I | TWO-DIGIT "SPECIAL" CODE

(

*Two-digit special codes assigned by Mercer Valve, if applicable.*)^{★}Standard Materials or Options.

Inlet and Outlet Code | Inlet and Outlet Size (in) | Pressure Limit^{ 1, 2}(psig) | Dimensions^{ 2}
"A" x "B" x "C" (in ± .062) | Approximate Weight^{ 2}(lbs) |
---|---|---|---|---|

Inlet and Outlet Code05 | Inlet and Outlet Size (in)½" 150 x 1" 150 | Pressure Limit^{ 1, 2}(psig)285 | Dimensions^{ 2}
"A" x "B" x "C" (in ± .062)3.375 x 4.500 x 8.188 | Approximate Weight^{ 2}(lbs) |

Inlet and Outlet Code06 | Inlet and Outlet Size (in)½" 3000 x 1" 150 | Pressure Limit^{ 1, 2}(psig)740 | Dimensions^{ 2}
"A" x "B" x "C" (in ± .062)3.375 x 4.500 x 8.188 | Approximate Weight^{ 2}(lbs) |

Inlet and Outlet Code07 | Inlet and Outlet Size (in)½" 600 x 1" 150 | Pressure Limit^{ 1, 2}(psig)1480 | Dimensions^{ 2}
"A" x "B" x "C" (in ± .062)3.375 x 4.500 x 8.188 | Approximate Weight^{ 2}(lbs) |

Inlet and Outlet Code08 | Inlet and Outlet Size (in)½" 900 x 1" 300 | Pressure Limit^{ 1, 2}(psig)2220 | Dimensions^{ 2}
"A" x "B" x "C" (in ± .062)3.750 x 4.500 x 8.563 | Approximate Weight^{ 2}(lbs) |

Inlet and Outlet Code09 | Inlet and Outlet Size (in)½" 1500 x 1" 300 | Pressure Limit^{ 1, 2}(psig)2999 | Dimensions^{ 2}
"A" x "B" x "C" (in ± .062)3.750 x 4.500 x 8.563 | Approximate Weight^{ 2}(lbs) |

Inlet and Outlet Code11^{★} | Inlet and Outlet Size (in)¾" 150 x 1" 150 | Pressure Limit^{ 1, 2}(psig)285 | Dimensions^{ 2}
"A" x "B" x "C" (in ± .062)4.125 x 4.500 x 8.938 | Approximate Weight^{ 2}(lbs) 9 |

Inlet and Outlet Code12^{★} | Inlet and Outlet Size (in)¾" 300 x 1" 150 | Pressure Limit^{ 1, 2}(psig)740 | Dimensions^{ 2}
"A" x "B" x "C" (in ± .062)4.125 x 4.500 x 8.938 | Approximate Weight^{ 2}(lbs) 10 |

Inlet and Outlet Code13^{★} | Inlet and Outlet Size (in)¾" 600 x 1" 150 | Pressure Limit^{ 1, 2}(psig)1480 | Dimensions^{ 2}
"A" x "B" x "C" (in ± .062)4.125 x 4.500 x 8.938 | Approximate Weight^{ 2}(lbs) 11 |

Inlet and Outlet Code14^{★} | Inlet and Outlet Size (in)¾" 900 x 1" 300 | Pressure Limit^{ 1, 2}(psig)2220 | Dimensions^{ 2}
"A" x "B" x "C" (in ± .062)4.125 x 4.500 x 8.938 | Approximate Weight^{ 2}(lbs) 14 |

Inlet and Outlet Code15^{★} | Inlet and Outlet Size (in)¾" 1500 x 1" 300 | Pressure Limit^{ 1, 2}(psig)2999 | Dimensions^{ 2}
"A" x "B" x "C" (in ± .062)4.125 x 4.500 x 8.938 | Approximate Weight^{ 2}(lbs) 14 |

Inlet and Outlet Code16^{★} | Inlet and Outlet Size (in)1" 150 x 1" 150 | Pressure Limit^{ 1, 2}(psig)285 | Dimensions^{ 2}
"A" x "B" x "C" (in ± .062)4.125 x 4.500 x 8.938 | Approximate Weight^{ 2}(lbs) 12 |

Inlet and Outlet Code17^{★} | Inlet and Outlet Size (in)1" 300 x 1" 150 | Pressure Limit^{ 1, 2}(psig)740 | Dimensions^{ 2}
"A" x "B" x "C" (in ± .062)4.125 x 4.500 x 8.938 | Approximate Weight^{ 2}(lbs) 13 |

Inlet and Outlet Code18^{★} | Inlet and Outlet Size (in)1" 600 x 1" 150 | Pressure Limit^{ 1, 2}(psig)1480 | Dimensions^{ 2}
"A" x "B" x "C" (in ± .062)4.125 x 4.500 x 8.938 | Approximate Weight^{ 2}(lbs) 14 |

Inlet and Outlet Code19^{★} | Inlet and Outlet Size (in)1" 900 x 1" 300 | Pressure Limit^{ 1, 2}(psig)2220 | Dimensions^{ 2}
"A" x "B" x "C" (in ± .062)4.125 x 4.500 x 8.938 | Approximate Weight^{ 2}(lbs) 18 |

Inlet and Outlet Code21^{★} | Inlet and Outlet Size (in)1" 1500 x 1" 300 | Pressure Limit^{ 1, 2}(psig)2999 | Dimensions^{ 2}
"A" x "B" x "C" (in ± .062)4.125 x 4.500 x 8.938 | Approximate Weight^{ 2}(lbs) 18 |

Inlet and Outlet Code22 | Inlet and Outlet Size (in)1" 150 x 1 ½" 150 | Pressure Limit^{ 1, 2}(psig)285 | Dimensions^{ 2}
"A" x "B" x "C" (in ± .062)4.125 x 4.500 x 8.938 | Approximate Weight^{ 2}(lbs) 11 |

Inlet and Outlet Code23 | Inlet and Outlet Size (in)1" 300 x 1 ½" 150 | Pressure Limit^{ 1, 2}(psig)740 | Dimensions^{ 2}
"A" x "B" x "C" (in ± .062)4.125 x 4.500 x 8.938 | Approximate Weight^{ 2}(lbs) 13 |

Inlet and Outlet Code24 | Inlet and Outlet Size (in)1" 600 x 1 ½" 150 | Pressure Limit^{ 1, 2}(psig)1480 | Dimensions^{ 2}
"A" x "B" x "C" (in ± .062)4.875 x 4.500 x 10.500 | Approximate Weight^{ 2}(lbs) 13 |

Inlet and Outlet Code25 | Inlet and Outlet Size (in)1" 900 x 1 ½" 300 | Pressure Limit^{ 1, 2}(psig)2220 | Dimensions^{ 2}
"A" x "B" x "C" (in ± .062)5.250 x 5.500 x 10.875 | Approximate Weight^{ 2}(lbs) 27 |

Inlet and Outlet Code26 | Inlet and Outlet Size (in)1" 1500 x 1 ½" 300 | Pressure Limit^{ 1, 2}(psig)2999 | Dimensions^{ 2}
"A" x "B" x "C" (in ± .062)5.250 x 5.500 x 10.875 | Approximate Weight^{ 2}(lbs) 27 |

Inlet and Outlet Code27 | Inlet and Outlet Size (in)1" 150 x 2" 150 | Pressure Limit^{ 1, 2}(psig)285 | Dimensions^{ 2}
"A" x "B" x "C" (in ± .062)4.125 x 4.500 x 8.938 | Approximate Weight^{ 2}(lbs) 14 |

Inlet and Outlet Code28 | Inlet and Outlet Size (in)1" 300 x 2" 150 | Pressure Limit^{ 1, 2}(psig)740 | Dimensions^{ 2}
"A" x "B" x "C" (in ± .062)4.125 x 4.500 x 8.938 | Approximate Weight^{ 2}(lbs) 15 |

Inlet and Outlet Code29 | Inlet and Outlet Size (in)1" 600 x 2" 150 | Pressure Limit^{ 1, 2}(psig)1480 | Dimensions^{ 2}
"A" x "B" x "C" (in ± .062)4.125 x 4.500 x 8.938 | Approximate Weight^{ 2}(lbs) 15 |

Inlet and Outlet Code31 | Inlet and Outlet Size (in)1" 900 x 2" 300 | Pressure Limit^{ 1, 2}(psig)2220 | Dimensions^{ 2}
"A" x "B" x "C" (in ± .062)5.250 x 5.500 x 10.875 | Approximate Weight^{ 2}(lbs) 28 |

Inlet and Outlet Code32 | Inlet and Outlet Size (in)1" 1500 x 2" 300 | Pressure Limit^{ 1, 2}(psig)2999 | Dimensions^{ 2}
"A" x "B" x "C" (in ± .062)5.250 x 5.500 x 10.875 | Approximate Weight^{ 2}(lbs) 28 |

Inlet and Outlet Code33 | Inlet and Outlet Size (in)1 ½" 150 x 2" 150 | Pressure Limit^{ 1, 2}(psig)285 | Dimensions^{ 2}
"A" x "B" x "C" (in ± .062)4.875 x 4.750 x 10.500 | Approximate Weight^{ 2}(lbs) 22 |

Inlet and Outlet Code34 | Inlet and Outlet Size (in)1 ½" 300 x 2" 150 | Pressure Limit^{ 1, 2}(psig)740 | Dimensions^{ 2}
"A" x "B" x "C" (in ± .062)4.875 x 6.000 x 10.500 | Approximate Weight^{ 2}(lbs) 25 |

Inlet and Outlet Code35 | Inlet and Outlet Size (in)1 ½" 600 x 2" 150 | Pressure Limit^{ 1, 2}(psig)1480 | Dimensions^{ 2}
"A" x "B" x "C" (in ± .062)4.875 x 6.000 x 10.500 | Approximate Weight^{ 2}(lbs) 26 |

Inlet and Outlet Code36 | Inlet and Outlet Size (in)1 ½" 900 x 2" 300 | Pressure Limit^{ 1, 2}(psig)2220 | Dimensions^{ 2}
"A" x "B" x "C" (in ± .062)4.125 x 5.500 x 9.748 | Approximate Weight^{ 2}(lbs) 31 |

Inlet and Outlet Code92 | Inlet and Outlet Size (in)1 ½" 1500 x 2" 300 | Pressure Limit^{ 1, 2}(psig)2999 | Dimensions^{ 2}
"A" x "B" x "C" (in ± .062)4.125 x 5.500 x 9.748 | Approximate Weight^{ 2}(lbs) 31 |

Inlet and Outlet Code42 | Inlet and Outlet Size (in)2" 150 x 2" 150 | Pressure Limit^{ 1, 2}(psig)285 | Dimensions^{ 2}
"A" x "B" x "C" (in ± .062)4.875 x 4.750 x 10.500 | Approximate Weight^{ 2}(lbs) 24 |

Inlet and Outlet Code43 | Inlet and Outlet Size (in)2" 300 x 2" 150 | Pressure Limit^{ 1, 2}(psig)740 | Dimensions^{ 2}
"A" x "B" x "C" (in ± .062)4.875 x 4.750 x 10.500 | Approximate Weight^{ 2}(lbs) 26 |

Inlet and Outlet Code44 | Inlet and Outlet Size (in)2" 600 x 2" 150 | Pressure Limit^{ 1, 2}(psig)1480 | Dimensions^{ 2}
"A" x "B" x "C" (in ± .062)5.375 x 6.000 x 11.000 | Approximate Weight^{ 2}(lbs) 29 |

Inlet and Outlet Code45 | Inlet and Outlet Size (in)2" 900 x 2" 300 | Pressure Limit^{ 1, 2}(psig)2220 | Dimensions^{ 2}
"A" x "B" x "C" (in ± .062)6.063 x 6.000 x 11.688 | Approximate Weight^{ 2}(lbs) 46 |

Inlet and Outlet Code95 | Inlet and Outlet Size (in)2" 1500 x 2" 300 | Pressure Limit^{ 1, 2}(psig)2999 | Dimensions^{ 2}
"A" x "B" x "C" (in ± .062)6.063 x 6.000 x 11.688 | Approximate Weight^{ 2}(lbs) |

^{1}Pressure limit may be subject to system conditions and temperatures.

^{2}Pressure limit, weight, and “C” dimension may vary with sour gas service and other options.

^{★}Standard Materials or Options.

Inlet and Outlet Code | Inlet and Outlet Size DN (mm) | Pressure Limit^{1, 2}(kPa) | Dimensions^{2}
"A" x "B" x "C" (mm ± 1.6) | Approximate Weight^{2}(kg) |
---|---|---|---|---|

Inlet and Outlet Code05 | Inlet and Outlet Size DN (mm)DN 15 150 x DN 25 150 | Pressure Limit^{1, 2}(kPa)1965 | Dimensions^{2}
"A" x "B" x "C" (mm ± 1.6)85.7 x 114.3 x 208.0 | Approximate Weight^{2}(kg) |

Inlet and Outlet Code06 | Inlet and Outlet Size DN (mm)DN 15 300 x DN 25 150 | Pressure Limit^{1, 2}(kPa)5102 | Dimensions^{2}
"A" x "B" x "C" (mm ± 1.6)85.7 x 114.3 x 208.0 | Approximate Weight^{2}(kg) |

Inlet and Outlet Code07 | Inlet and Outlet Size DN (mm)DN 15 600 x DN 25 150 | Pressure Limit^{1, 2}(kPa)10204 | Dimensions^{2}
"A" x "B" x "C" (mm ± 1.6)85.7 x 114.3 x 208.0 | Approximate Weight^{2}(kg) |

Inlet and Outlet Code08 | Inlet and Outlet Size DN (mm)DN 15 900 x DN 25 300 | Pressure Limit^{1, 2}(kPa)15306 | Dimensions^{2}
"A" x "B" x "C" (mm ± 1.6)95.3 x 114.3 x 217.5 | Approximate Weight^{2}(kg) |

Inlet and Outlet Code09 | Inlet and Outlet Size DN (mm)DN 15 1500 x DN 25 300 | Pressure Limit^{1, 2}(kPa)20677 | Dimensions^{2}
"A" x "B" x "C" (mm ± 1.6)95.3 x 114.3 x 217.5 | Approximate Weight^{2}(kg) |

Inlet and Outlet Code11^{★} | Inlet and Outlet Size DN (mm)DN 20 150 x DN 25 150 | Pressure Limit^{1, 2}(kPa)1965 | Dimensions^{2}
"A" x "B" x "C" (mm ± 1.6)104.8 x 114.3 x 228.6 | Approximate Weight^{2}(kg)4.1 |

Inlet and Outlet Code12^{★} | Inlet and Outlet Size DN (mm)DN 20 300 x DN 25 150 | Pressure Limit^{1, 2}(kPa)5102 | Dimensions^{2}
"A" x "B" x "C" (mm ± 1.6)104.8 x 114.3 x 228.6 | Approximate Weight^{2}(kg)4.5 |

Inlet and Outlet Code13^{★} | Inlet and Outlet Size DN (mm)DN 20 600 x DN 25 150 | Pressure Limit^{1, 2}(kPa)10204 | Dimensions^{2}
"A" x "B" x "C" (mm ± 1.6)104.8 x 114.3 x 228.6 | Approximate Weight^{2}(kg)5.0 |

Inlet and Outlet Code14^{★} | Inlet and Outlet Size DN (mm)DN 20 900 x DN 25 300 | Pressure Limit^{1, 2}(kPa)15306 | Dimensions^{2}
"A" x "B" x "C" (mm ± 1.6)104.8 x 114.3 x 228.6 | Approximate Weight^{2}(kg)6.4 |

Inlet and Outlet Code15^{★} | Inlet and Outlet Size DN (mm)DN 20 1500 x DN 25 300 | Pressure Limit^{1, 2}(kPa)20677 | Dimensions^{2}
"A" x "B" x "C" (mm ± 1.6)104.8 x 114.3 x 228.6 | Approximate Weight^{2}(kg)6.4 |

Inlet and Outlet Code16^{★} | Inlet and Outlet Size DN (mm)DN 25 150 x DN 25 150 | Pressure Limit^{1, 2}(kPa)1965 | Dimensions^{2}
"A" x "B" x "C" (mm ± 1.6)104.8 x 114.3 x 228.6 | Approximate Weight^{2}(kg)4.1 |

Inlet and Outlet Code17^{★} | Inlet and Outlet Size DN (mm)DN 25 300 x DN 25 150 | Pressure Limit^{1, 2}(kPa)5102 | Dimensions^{2}
"A" x "B" x "C" (mm ± 1.6)104.8 x 114.3 x 228.6 | Approximate Weight^{2}(kg)5.0 |

Inlet and Outlet Code18^{★} | Inlet and Outlet Size DN (mm)DN 25 600 x DN 25 150 | Pressure Limit^{1, 2}(kPa)10204 | Dimensions^{2}
"A" x "B" x "C" (mm ± 1.6)104.8 x 114.3 x 228.6 | Approximate Weight^{2}(kg)5.0 |

Inlet and Outlet Code19^{★} | Inlet and Outlet Size DN (mm)DN 25 900 x DN 25 300 | Pressure Limit^{1, 2}(kPa)15306 | Dimensions^{2}
"A" x "B" x "C" (mm ± 1.6)104.8 x 114.3 x 228.6 | Approximate Weight^{2}(kg)7.3 |

Inlet and Outlet Code21^{★} | Inlet and Outlet Size DN (mm)DN 25 1500 x DN 25 300 | Pressure Limit^{1, 2}(kPa)20677 | Dimensions^{2}
"A" x "B" x "C" (mm ± 1.6)104.8 x 114.3 x 228.6 | Approximate Weight^{2}(kg)7.3 |

Inlet and Outlet Code22 | Inlet and Outlet Size DN (mm)DN 25 150 x DN 40 150 | Pressure Limit^{1, 2}(kPa)1965 | Dimensions^{2}
"A" x "B" x "C" (mm ± 1.6)104.8 x 114.3 x 228.6 | Approximate Weight^{2}(kg)5.0 |

Inlet and Outlet Code23 | Inlet and Outlet Size DN (mm)DN 25 300 x DN 40 150 | Pressure Limit^{1, 2}(kPa)5102 | Dimensions^{2}
"A" x "B" x "C" (mm ± 1.6)104.8 x 114.3 x 228.6 | Approximate Weight^{2}(kg)5.9 |

Inlet and Outlet Code24 | Inlet and Outlet Size DN (mm)DN 25 600 x DN 40 150 | Pressure Limit^{1, 2}(kPa)10204 | Dimensions^{2}
"A" x "B" x "C" (mm ± 1.6)123.8 x 114.3 x 266.7 | Approximate Weight^{2}(kg)5.9 |

Inlet and Outlet Code25 | Inlet and Outlet Size DN (mm)DN 25 900 x DN 40 300 | Pressure Limit^{1, 2}(kPa)15306 | Dimensions^{2}
"A" x "B" x "C" (mm ± 1.6)149.2 x 139.7 x 292.1 | Approximate Weight^{2}(kg)12.2 |

Inlet and Outlet Code26 | Inlet and Outlet Size DN (mm)DN 25 1500 x DN 40 300 | Pressure Limit^{1, 2}(kPa)20677 | Dimensions^{2}
"A" x "B" x "C" (mm ± 1.6)149.2 x 139.7 x 292.1 | Approximate Weight^{2}(kg)12.2 |

Inlet and Outlet Code27 | Inlet and Outlet Size DN (mm)DN 25 150 x DN 50 150 | Pressure Limit^{1, 2}(kPa)1965 | Dimensions^{2}
"A" x "B" x "C" (mm ± 1.6)104.8 x 114.3 x 228.6 | Approximate Weight^{2}(kg)6.4 |

Inlet and Outlet Code28 | Inlet and Outlet Size DN (mm)DN 25 300 x DN 50 150 | Pressure Limit^{1, 2}(kPa)5102 | Dimensions^{2}
"A" x "B" x "C" (mm ± 1.6)104.8 x 114.3 x 228.6 | Approximate Weight^{2}(kg)6.8 |

Inlet and Outlet Code29 | Inlet and Outlet Size DN (mm)DN 25 600 x DN 50 150 | Pressure Limit^{1, 2}(kPa)10204 | Dimensions^{2}
"A" x "B" x "C" (mm ± 1.6)104.8 x 114.3 x 228.6 | Approximate Weight^{2}(kg)6.8 |

Inlet and Outlet Code31 | Inlet and Outlet Size DN (mm)DN 25 900 x DN 50 300 | Pressure Limit^{1, 2}(kPa)15306 | Dimensions^{2}
"A" x "B" x "C" (mm ± 1.6)133.4 x 139.7 x 276.2 | Approximate Weight^{2}(kg)12.7 |

Inlet and Outlet Code32 | Inlet and Outlet Size DN (mm)DN 25 1500 x DN 50 300 | Pressure Limit^{1, 2}(kPa)20677 | Dimensions^{2}
"A" x "B" x "C" (mm ± 1.6)133.4 x 139.7 x 276.2 | Approximate Weight^{2}(kg)12.7 |

Inlet and Outlet Code33 | Inlet and Outlet Size DN (mm)DN 40 150 x DN 50 150 | Pressure Limit^{1, 2}(kPa)1965 | Dimensions^{2}
"A" x "B" x "C" (mm ± 1.6)123.8 x 120.7 x 266.7 | Approximate Weight^{2}(kg)10.0 |

Inlet and Outlet Code34 | Inlet and Outlet Size DN (mm)DN 40 300 x DN 50 150 | Pressure Limit^{1, 2}(kPa)5102 | Dimensions^{2}
"A" x "B" x "C" (mm ± 1.6)123.8 x 120.7 x 266.7 | Approximate Weight^{2}(kg)11.3 |

Inlet and Outlet Code35 | Inlet and Outlet Size DN (mm)DN 40 600 x DN 50 150 | Pressure Limit^{1, 2}(kPa)10204 | Dimensions^{2}
"A" x "B" x "C" (mm ± 1.6)123.8 x 120.7 x 266.7 | Approximate Weight^{2}(kg)11.8 |

Inlet and Outlet Code36 | Inlet and Outlet Size DN (mm)DN 40 900 x DN 50 300 | Pressure Limit^{1, 2}(kPa)15306 | Dimensions^{2}
"A" x "B" x "C" (mm ± 1.6)104.8 x 139.7 x 247.7 | Approximate Weight^{2}(kg)14.1 |

Inlet and Outlet Code92 | Inlet and Outlet Size DN (mm)DN 40 1500 x DN 50 300 | Pressure Limit^{1, 2}(kPa)20677 | Dimensions^{2}
"A" x "B" x "C" (mm ± 1.6)104.8 x 139.7 x 247.7 | Approximate Weight^{2}(kg)14.1 |

Inlet and Outlet Code42 | Inlet and Outlet Size DN (mm)DN 50 150 x DN 50 150 | Pressure Limit^{1, 2}(kPa)1965 | Dimensions^{2}
"A" x "B" x "C" (mm ± 1.6)123.8 x 120.7 x 266.7 | Approximate Weight^{2}(kg)10.9 |

Inlet and Outlet Code43 | Inlet and Outlet Size DN (mm)DN 50 300 x DN 50 150 | Pressure Limit^{1, 2}(kPa)5102 | Dimensions^{2}
"A" x "B" x "C" (mm ± 1.6)123.8 x 120.7 x 266.7 | Approximate Weight^{2}(kg)11.8 |

Inlet and Outlet Code44 | Inlet and Outlet Size DN (mm)DN 50 600 x DN 50 150 | Pressure Limit^{1, 2}(kPa)10204 | Dimensions^{2}
"A" x "B" x "C" (mm ± 1.6)136.5 x 152.4 x 279.4 | Approximate Weight^{2}(kg)13.2 |

Inlet and Outlet Code45 | Inlet and Outlet Size DN (mm)DN 50 900 x DN 50 300 | Pressure Limit^{1, 2}(kPa)15306 | Dimensions^{2}
"A" x "B" x "C" (mm ± 1.6)154.0 x 152.4 x 296.9 | Approximate Weight^{2}(kg)20.9 |

Inlet and Outlet Code95 | Inlet and Outlet Size DN (mm)DN 50 1500 x DN 50 300 | Pressure Limit^{1, 2}(kPa)20677 | Dimensions^{2}
"A" x "B" x "C" (mm ± 1.6)154.0 x 152.4 x 296.9 | Approximate Weight^{2}(kg) |

^{1}Pressure limit may be subject to system conditions and temperatures.

^{2}Pressure limit, weight, and “C” dimension may vary with sour gas service and other options.

^{★}Standard Materials or Options.