## think…mercer first^{®}

### Features:

- Designed with "Auto Seat Technology"®
- A low rated and fully guided spring allows for more consistent Set Pressures from pop to pop.
- Consistent Set Pressures allows for repeatable use without the need for excessive repairs or resetting.
- Open, Close, Seat and Seal™
- Fully guided disk for the proper alignment, opening and closing, and reseating of the valve.
- Mechanical Stop prevents wear on parts and controls valve lift.
- Pop Action relief allows the valve to go to full lift at Set Pressure. This helps with DOT regulated applications.
- Non-rising stems allowing valves to be installed in small areas.

Orifice | F
(USC) | F
(SI) |
---|---|---|

OrificeStandard Inlet Sizes | F
(USC) 1", 1 ½" | F
(SI) DN 25, DN 40 |

OrificeInlet and Outlet Connection Types | F
(USC) RF x RF, RTJ x RF, RTJ x RTJ | F
(SI) RF x RF, RTJ x RF, RTJ x RTJ |

OrificeActual Orifice Diameter | F
(USC) 0.655 in | F
(SI) 16.6 mm |

OrificeActual Orifice Area | F
(USC) 0.337 in ^{2} | F
(SI) 217.4 mm ^{2} |

OrificeAPI Orifice Area | F
(USC) 0.307 in ^{2} | F
(SI) 198.1 mm ^{2} |

OrificePressure Range | F
(USC) 15 – 2400 psig | F
(SI) 104 – 16547 kPa |

OrificeStandard Temperature Range | F
(USC) -20°F to 400°F | F
(SI) -29°C to 204°C |

OrificeASME Flow Coefficient, K_{d} (Gas) | F
(USC) 0.818 | F
(SI) 0.818 |

OrificeASME Flow Coefficient, K_{d} (Liquid) | F
(USC) 0.707 | F
(SI) 0.707 |

*Mercer Valve Co., Inc. reserves the right to change product designs and specifications without notice.*

### 9100 Flanged "F" | Part Number Selection

91 -

23

A

F

B

1

C

1

D

T

E

11

F

U

G

1

H

I

### A | INLET & OUTLET COMBINATION

(

*See*)**Dimensions & Weights**, below.### B | API ORIFICE LETTER

**F**– 0.337 in²

### C | INLET & OUTLET TYPE / BODY MATERIAL

**1**

^{★}– RF x RF / WCB CARBON STEEL

**3**

^{★}– RTJ x RF / WCB CARBON STEEL

**2**– RF x RF / CF3M STAINLESS STEEL

**4**– RTJ x RF / CF3M STAINLESS STEEL

**A**– RTJ x RTJ / WCB CARBON STEEL

**B**– RTJ x RTJ / CF3M STAINLESS STEEL

**P**– RF x RF / LCC TEMP CARBON STEEL

**Q**– RTJ x RF / LCC TEMP CARBON STEEL

### D | CAP TYPE

**1**

^{★}– CLOSED CAP

**2**– OPEN LIFT LEVER

**3**– CLOSED LIFT LEVER

### E | SEAT MATERIAL

**V**

^{★}– FKM

**T**

^{★}– PTFE

**P**

^{★}– VIRGIN PEEK

**B**– BUNA-N

**E**– EPDM

**N**– NEOPRENE

**X**– FFKM

**Y**– VESPEL®

**L**– PC BUNA

**F**– FKM (LOW TEMP)

### F | SPRING CODE

(

*Spring codes assigned by Mercer Valve.*)### G | TRIM CODES

**U**

^{★}– 316 S.S. DISK & NOZZLE (GAS SERVICE ≤ 1450 PSIG)

**C**

^{★}– 440C S.S. DISK, 17-4 S.S. NOZZLE (GAS SERVICE > 1450 PSIG)

**L**

^{★}– 316 S.S. DISK & NOZZLE (LIQUID SERVICE)

**N**

^{★}– 316 S.S. DISK & NOZZLE (SOUR GAS SERVICE)

**B**

^{★}– 316 S.S. DISK & NOZZLE (SOUR LIQUID SERVICE)

**X**– ALL 316 S.S. (OPTIONAL GAS SERVICE)

**LX**– ALL 316 S.S. (OPTIONAL LIQUID SERVICE)

**BX**– ALL 316 S.S. (OPTIONAL SOUR LIQUID SERVICE)

**NX**– ALL 316 S.S. (OPTIONAL SOUR GAS SERVICE)

### H | O-RING MATERIAL

**1**

^{★}– FKM & BUNA-N (STANDARD)

**2**– FKM 75 DURO

**3**– FKM 90 DURO

**4**– BUNA-N 70 DURO

**5**– BUNA-N 75 DURO (LOW TEMP)

**7**– FFKM

**9**– NEOPRENE

**A**– CHEMRAZ®

**C**– EPDM 80 DURO

**D**– EPDM 90 DURO

**G**– TFE/P

**H**– SILICONE

**J**– FLUOROSILICONE

**K**– HNBR

**L**– PC BUNA

**M**– FKM ED

**P**– FKM 75 DURO (LOW TEMP)

### I | TWO-DIGIT "SPECIAL" CODE

(

*Two-digit special codes assigned by Mercer Valve, if applicable.*)^{★}Standard Materials or Options.

Inlet and Outlet Code | Inlet and Outlet Size (in) | Pressure Limit^{1, 2}(psig) | Dimensions^{2}
"A" x "B" x "C" (in ± .062) | Approximate Weight^{2}(lbs) |
---|---|---|---|---|

Inlet and Outlet Code22 | Inlet and Outlet Size (in) 1" 150 x 1 ½" 150 | Pressure Limit^{1, 2}(psig) 285 | Dimensions^{2}
"A" x "B" x "C" (in ± .062) 4.125 x 4.750 x 9.750 | Approximate Weight^{2}(lbs) 19 |

Inlet and Outlet Code23 | Inlet and Outlet Size (in) 1" 300 x 1 ½" 150 | Pressure Limit^{1, 2}(psig) 740 | Dimensions^{2}
"A" x "B" x "C" (in ± .062) 4.500 x 4.750 x 10.125 | Approximate Weight^{2}(lbs) 20 |

Inlet and Outlet Code24 | Inlet and Outlet Size (in) 1" 600 x 1 ½" 150 | Pressure Limit^{1, 2}(psig) 1450 | Dimensions^{2}
"A" x "B" x "C" (in ± .062) 5.250 x 4.750 x 10.875 | Approximate Weight^{2}(lbs) 14 |

Inlet and Outlet Code27 | Inlet and Outlet Size (in) 1" 150 x 2" 150 | Pressure Limit^{1, 2}(psig) 285 | Dimensions^{2}
"A" x "B" x "C" (in ± .062) 4.125 x 4.500 x 9.750 | Approximate Weight^{2}(lbs) |

Inlet and Outlet Code28 | Inlet and Outlet Size (in) 1" 300 x 2" 150 | Pressure Limit^{1, 2}(psig) 740 | Dimensions^{2}
"A" x "B" x "C" (in ± .062) 4.500 x 4.500 x 10.125 | Approximate Weight^{2}(lbs) |

Inlet and Outlet Code29 | Inlet and Outlet Size (in) 1" 600 x 2" 150 | Pressure Limit^{1, 2}(psig) 1450 | Dimensions^{2}
"A" x "B" x "C" (in ± .062) 5.250 x 4.500 x 10.875 | Approximate Weight^{2}(lbs) |

Inlet and Outlet Code33^{★}^{☆} | Inlet and Outlet Size (in) 1 ½" 150 x 2" 150 | Pressure Limit^{1, 2}(psig) 285 | Dimensions^{2}
"A" x "B" x "C" (in ± .062) 4.875 x 4.750 x 10.500 | Approximate Weight^{2}(lbs) 22 |

Inlet and Outlet Code34^{★}^{☆} | Inlet and Outlet Size (in) 1 ½" 300 x 2" 150 | Pressure Limit^{1, 2}(psig) 740 | Dimensions^{2}
"A" x "B" x "C" (in ± .062) 4.875 x 6.000 x 10.500 | Approximate Weight^{2}(lbs) 25 |

Inlet and Outlet Code35^{★}^{☆} | Inlet and Outlet Size (in) 1 ½" 600 x 2" 150 | Pressure Limit^{1, 2}(psig) 1480 | Dimensions^{2}
"A" x "B" x "C" (in ± .062) 4.875 x 6.000 x 10.500 | Approximate Weight^{2}(lbs) 26 |

Inlet and Outlet Code36^{★} | Inlet and Outlet Size (in) 1 ½" 900 x 2" 300 | Pressure Limit^{1, 2}(psig) 2220 | Dimensions^{2}
"A" x "B" x "C" (in ± .062) 5.875 x 6.000 x 11.500 | Approximate Weight^{2}(lbs) 34 |

Inlet and Outlet Code92^{★} | Inlet and Outlet Size (in) 1 ½" 1500 x 2" 300 | Pressure Limit^{1, 2}(psig) 2400 | Dimensions^{2}
"A" x "B" x "C" (in ± .062) 5.875 x 6.000 x 11.500 | Approximate Weight^{2}(lbs) |

Inlet and Outlet Code37 | Inlet and Outlet Size (in) 1 ½" 150 x 2 ½" 150 | Pressure Limit^{1, 2}(psig) 285 | Dimensions^{2}
"A" x "B" x "C" (in ± .062) 4.875 x 4.750 x 10.500 | Approximate Weight^{2}(lbs) |

Inlet and Outlet Code38 | Inlet and Outlet Size (in) 1 ½" 300 x 2 ½" 150 | Pressure Limit^{1, 2}(psig) 740 | Dimensions^{2}
"A" x "B" x "C" (in ± .062) 4.875 x 4.750 x 10.500 | Approximate Weight^{2}(lbs) |

Inlet and Outlet Code39 | Inlet and Outlet Size (in) 1 ½" 600 x 2 ½" 150 | Pressure Limit^{1, 2}(psig) 1480 | Dimensions^{2}
"A" x "B" x "C" (in ± .062) 4.875 x 6.000 x 10.500 | Approximate Weight^{2}(lbs) |

Inlet and Outlet Code41 | Inlet and Outlet Size (in) 1 ½" 900 x 2 ½" 300 | Pressure Limit^{1, 2}(psig) 2220 | Dimensions^{2}
"A" x "B" x "C" (in ± .062) 5.875 x 6.000 x 11.500 | Approximate Weight^{2}(lbs) |

Inlet and Outlet Code93 | Inlet and Outlet Size (in) 1 ½" 1500 x 2 ½" 300 | Pressure Limit^{1, 2}(psig) 2400 | Dimensions^{2}
"A" x "B" x "C" (in ± .062) 5.875 x 6.000 x 11.500 | Approximate Weight^{2}(lbs) |

Inlet and Outlet Code55 | Inlet and Outlet Size (in) 1 ½" 150 x 3" 150 | Pressure Limit^{1, 2}(psig) 285 | Dimensions^{2}
"A" x "B" x "C" (in ± .062) 4.875 x 4.750 x 10.500 | Approximate Weight^{2}(lbs) |

Inlet and Outlet Code56 | Inlet and Outlet Size (in) 1 ½" 300 x 3" 150 | Pressure Limit^{1, 2}(psig) 740 | Dimensions^{2}
"A" x "B" x "C" (in ± .062) 4.875 x 6.000 x 10.500 | Approximate Weight^{2}(lbs) |

Inlet and Outlet Code74 | Inlet and Outlet Size (in) 1 ½" 600 x 3" 150 | Pressure Limit^{1, 2}(psig) 1480 | Dimensions^{2}
"A" x "B" x "C" (in ± .062) 4.875 x 6.000 x 10.500 | Approximate Weight^{2}(lbs) |

Inlet and Outlet Code75^{★}^{☆} | Inlet and Outlet Size (in) 1 ½" 900 x 3" 300 | Pressure Limit^{1, 2}(psig) 2220 | Dimensions^{2}
"A" x "B" x "C" (in ± .062) 4.875 x 6.500 x 10.498 | Approximate Weight^{2}(lbs) 44 |

Inlet and Outlet Code94^{★}^{☆} | Inlet and Outlet Size (in) 1 ½" 1500 x 3" 300 | Pressure Limit^{1, 2}(psig) 2400 | Dimensions^{2}
"A" x "B" x "C" (in ± .062) 6.063 x 6.000 x 11.688 | Approximate Weight^{2}(lbs) 44 |

Inlet and Outlet Code42 | Inlet and Outlet Size (in) 2" 150 x 2" 150 | Pressure Limit^{1, 2}(psig) 285 | Dimensions^{2}
"A" x "B" x "C" (in ± .062) 4.875 x 4.750 x 10.500 | Approximate Weight^{2}(lbs) 24 |

Inlet and Outlet Code43 | Inlet and Outlet Size (in) 2" 300 x 2" 150 | Pressure Limit^{1, 2}(psig) 740 | Dimensions^{2}
"A" x "B" x "C" (in ± .062) 4.875 x 4.750 x 10.500 | Approximate Weight^{2}(lbs) 26 |

Inlet and Outlet Code44 | Inlet and Outlet Size (in) 2" 600 x 2" 150 | Pressure Limit^{1, 2}(psig) 1480 | Dimensions^{2}
"A" x "B" x "C" (in ± .062) 5.375 x 6.000 x 11.000 | Approximate Weight^{2}(lbs) 29 |

Inlet and Outlet Code45 | Inlet and Outlet Size (in) 2" 900 x 2" 300 | Pressure Limit^{1, 2}(psig) 2220 | Dimensions^{2}
"A" x "B" x "C" (in ± .062) 6.063 x 6.000 x 11.688 | Approximate Weight^{2}(lbs) 46 |

Inlet and Outlet Code95 | Inlet and Outlet Size (in) 2" 1500 x 2" 300 | Pressure Limit^{1, 2}(psig) 2400 | Dimensions^{2}
"A" x "B" x "C" (in ± .062) 6.063 x 6.000 x 11.688 | Approximate Weight^{2}(lbs) |

Inlet and Outlet Code46 | Inlet and Outlet Size (in) 2" 150 x 2 ½" 150 | Pressure Limit^{1, 2}(psig) 285 | Dimensions^{2}
"A" x "B" x "C" (in ± .062) 4.875 x 4.750 x 10.500 | Approximate Weight^{2}(lbs) |

Inlet and Outlet Code47 | Inlet and Outlet Size (in) 2" 300 x 2 ½" 150 | Pressure Limit^{1, 2}(psig) 740 | Dimensions^{2}
"A" x "B" x "C" (in ± .062) 6.063 x 6.000 x 11.688 | Approximate Weight^{2}(lbs) |

Inlet and Outlet Code48 | Inlet and Outlet Size (in) 2" 600 x 2 ½" 150 | Pressure Limit^{1, 2}(psig) 1480 | Dimensions^{2}
"A" x "B" x "C" (in ± .062) 5.375 x 6.000 x 11.000 | Approximate Weight^{2}(lbs) |

Inlet and Outlet Code49 | Inlet and Outlet Size (in) 2" 900 x 2 ½" 300 | Pressure Limit^{1, 2}(psig) 2220 | Dimensions^{2}
"A" x "B" x "C" (in ± .062) 4.875 x 4.750 x 10.500 | Approximate Weight^{2}(lbs) |

Inlet and Outlet Code96 | Inlet and Outlet Size (in) 2" 1500 x 2 ½" 300 | Pressure Limit^{1, 2}(psig) 2400 | Dimensions^{2}
"A" x "B" x "C" (in ± .062) 6.063 x 6.000 x 11.688 | Approximate Weight^{2}(lbs) |

Inlet and Outlet Code51 | Inlet and Outlet Size (in) 2" 150 x 3" 150 | Pressure Limit^{1, 2}(psig) 285 | Dimensions^{2}
"A" x "B" x "C" (in ± .062) 4.875 x 5.375 x 10.500 | Approximate Weight^{2}(lbs) 30 |

Inlet and Outlet Code52 | Inlet and Outlet Size (in) 2" 300 x 3" 150 | Pressure Limit^{1, 2}(psig) 740 | Dimensions^{2}
"A" x "B" x "C" (in ± .062) 4.875 x 5.375 x 10.500 | Approximate Weight^{2}(lbs) 33 |

Inlet and Outlet Code53 | Inlet and Outlet Size (in) 2" 600 x 3" 150 | Pressure Limit^{1, 2}(psig) 1480 | Dimensions^{2}
"A" x "B" x "C" (in ± .062) 6.063 x 6.375 x 11.688 | Approximate Weight^{2}(lbs) 37 |

Inlet and Outlet Code54 | Inlet and Outlet Size (in) 2" 900 x 3" 300 | Pressure Limit^{1, 2}(psig) 2220 | Dimensions^{2}
"A" x "B" x "C" (in ± .062) 6.063 x 6.375 x 11.688 | Approximate Weight^{2}(lbs) 56 |

Inlet and Outlet Code97 | Inlet and Outlet Size (in) 2" 1500 x 3" 300 | Pressure Limit^{1, 2}(psig) 2400 | Dimensions^{2}
"A" x "B" x "C" (in ± .062) 6.063 x 6.375 x 11.688 | Approximate Weight^{2}(lbs) |

^{1}Pressure limit may be subject to system conditions and temperatures.

^{2}Pressure limit, weight, and “C” dimension may vary with sour gas service and other options.

^{★}Standard Materials or Options.

^{☆}Flange dimensions compliant with API 526.

Inlet and Outlet Code | Inlet and Outlet Size DN (mm) | Pressure Limit^{1, 2}(kPa) | Dimensions^{2}
"A" x "B" x "C" (mm ± 1.6) | Approximate Weight^{2}(kg) |
---|---|---|---|---|

Inlet and Outlet Code22 | Inlet and Outlet Size DN (mm)DN 25 150 x DN 40 150 | Pressure Limit^{1, 2}(kPa)1965 | Dimensions^{2}
"A" x "B" x "C" (mm ± 1.6) 104.8 x 120.7 x 247.7 | Approximate Weight^{2}(kg) 8.2 |

Inlet and Outlet Code23 | Inlet and Outlet Size DN (mm)DN 25 300 x DN 40 150 | Pressure Limit^{1, 2}(kPa)5102 | Dimensions^{2}
"A" x "B" x "C" (mm ± 1.6) 114.3 x 120.7 x 257.2 | Approximate Weight^{2}(kg) 8.6 |

Inlet and Outlet Code24 | Inlet and Outlet Size DN (mm)DN 25 600 x DN 40 150 | Pressure Limit^{1, 2}(kPa)9997 | Dimensions^{2}
"A" x "B" x "C" (mm ± 1.6) 133.4 x 120.7 x 276.2 | Approximate Weight^{2}(kg) 9.1 |

Inlet and Outlet Code27 | Inlet and Outlet Size DN (mm)DN 25 150 x DN 50 150 | Pressure Limit^{1, 2}(kPa)1965 | Dimensions^{2}
"A" x "B" x "C" (mm ± 1.6) 104.8 x 114.3 x 247.7 | Approximate Weight^{2}(kg) |

Inlet and Outlet Code28 | Inlet and Outlet Size DN (mm)DN 25 300 x DN 50 150 | Pressure Limit^{1, 2}(kPa)5102 | Dimensions^{2}
"A" x "B" x "C" (mm ± 1.6) 114.3 x 114.3 x 257.2 | Approximate Weight^{2}(kg) |

Inlet and Outlet Code29 | Inlet and Outlet Size DN (mm)DN 25 600 x DN 50 150 | Pressure Limit^{1, 2}(kPa)9997 | Dimensions^{2}
"A" x "B" x "C" (mm ± 1.6) 133.4 x 114.3 x 276.5 | Approximate Weight^{2}(kg) |

Inlet and Outlet Code33^{★}^{☆} | Inlet and Outlet Size DN (mm)DN 40 150 x DN 50 150 | Pressure Limit^{1, 2}(kPa)1965 | Dimensions^{2}
"A" x "B" x "C" (mm ± 1.6) 123.8 x 120.7 x 266.7 | Approximate Weight^{2}(kg) 10.0 |

Inlet and Outlet Code34^{★}^{☆} | Inlet and Outlet Size DN (mm)DN 40 300 x DN 50 150 | Pressure Limit^{1, 2}(kPa)5102 | Dimensions^{2}
"A" x "B" x "C" (mm ± 1.6) 123.8 x 152.4 x 266.7 | Approximate Weight^{2}(kg) 11.3 |

Inlet and Outlet Code35^{★}^{☆} | Inlet and Outlet Size DN (mm)DN 40 600 x DN 50 150 | Pressure Limit^{1, 2}(kPa)10204 | Dimensions^{2}
"A" x "B" x "C" (mm ± 1.6) 123.8 x 152.4 x 266.7 | Approximate Weight^{2}(kg) 11.8 |

Inlet and Outlet Code36^{★} | Inlet and Outlet Size DN (mm)DN 40 900 x DN 50 300 | Pressure Limit^{1, 2}(kPa)15168 | Dimensions^{2}
"A" x "B" x "C" (mm ± 1.6) 149.2 x 152.4 x 292.1 | Approximate Weight^{2}(kg) 15.4 |

Inlet and Outlet Code92^{★} | Inlet and Outlet Size DN (mm)DN 40 1500 x DN 50 300 | Pressure Limit^{1, 2}(kPa)16547 | Dimensions^{2}
"A" x "B" x "C" (mm ± 1.6) 149.2 x 152.4 x 292.1 | Approximate Weight^{2}(kg) |

Inlet and Outlet Code37 | Inlet and Outlet Size DN (mm)DN 40 150 x DN 65 150 | Pressure Limit^{1, 2}(kPa)1965 | Dimensions^{2}
"A" x "B" x "C" (mm ± 1.6) 123.8 x 120.7 x 266.7 | Approximate Weight^{2}(kg) |

Inlet and Outlet Code38 | Inlet and Outlet Size DN (mm)DN 40 300 x DN 65 150 | Pressure Limit^{1, 2}(kPa)5102 | Dimensions^{2}
"A" x "B" x "C" (mm ± 1.6) 123.8 x 120.7 x 266.7 | Approximate Weight^{2}(kg) |

Inlet and Outlet Code39 | Inlet and Outlet Size DN (mm)DN 40 600 x DN 65 150 | Pressure Limit^{1, 2}(kPa)10204 | Dimensions^{2}
"A" x "B" x "C" (mm ± 1.6) 123.8 x 152.4 x 266.7 | Approximate Weight^{2}(kg) |

Inlet and Outlet Code41 | Inlet and Outlet Size DN (mm)DN 40 900 x DN 65 300 | Pressure Limit^{1, 2}(kPa)150306 | Dimensions^{2}
"A" x "B" x "C" (mm ± 1.6) 149.2 x 152.4 x 292.1 | Approximate Weight^{2}(kg) |

Inlet and Outlet Code93 | Inlet and Outlet Size DN (mm)DN 40 1500 x DN 65 300 | Pressure Limit^{1, 2}(kPa)16547 | Dimensions^{2}
"A" x "B" x "C" (mm ± 1.6) 149.2 x 152.4 x 292.1 | Approximate Weight^{2}(kg) |

Inlet and Outlet Code55 | Inlet and Outlet Size DN (mm)DN 40 150 x DN 80 150 | Pressure Limit^{1, 2}(kPa)1965 | Dimensions^{2}
"A" x "B" x "C" (mm ± 1.6) 123.8 x 120.7 x 266.7 | Approximate Weight^{2}(kg) 12.2 |

Inlet and Outlet Code56 | Inlet and Outlet Size DN (mm)DN 40 300 x DN 80 150 | Pressure Limit^{1, 2}(kPa)5102 | Dimensions^{2}
"A" x "B" x "C" (mm ± 1.6) 123.8 x 152.4 x 266.7 | Approximate Weight^{2}(kg) 14.5 |

Inlet and Outlet Code74 | Inlet and Outlet Size DN (mm)DN 40 600 x DN 80 150 | Pressure Limit^{1, 2}(kPa)10204 | Dimensions^{2}
"A" x "B" x "C" (mm ± 1.6) 123.8 x 152.4 x 266.7 | Approximate Weight^{2}(kg) 15.0 |

Inlet and Outlet Code75^{★}^{☆} | Inlet and Outlet Size DN (mm)DN 40 900 x DN 80 300 | Pressure Limit^{1, 2}(kPa)15306 | Dimensions^{2}
"A" x "B" x "C" (mm ± 1.6) 123.8 x 165.1 x 266.7 | Approximate Weight^{2}(kg) 20.0 |

Inlet and Outlet Code94^{★}^{☆} | Inlet and Outlet Size DN (mm)DN 40 1500 x DN 80 300 | Pressure Limit^{1, 2}(kPa)16547 | Dimensions^{2}
"A" x "B" x "C" (mm ± 1.6) 123.8 x 165.1 x 266.7 | Approximate Weight^{2}(kg) 20.0 |

Inlet and Outlet Code42 | Inlet and Outlet Size DN (mm)DN 50 150 x DN 50 150 | Pressure Limit^{1, 2}(kPa)1965 | Dimensions^{2}
"A" x "B" x "C" (mm ± 1.6) 123.8 x 120.7 x 266.7 | Approximate Weight^{2}(kg) 10.9 |

Inlet and Outlet Code43 | Inlet and Outlet Size DN (mm)DN 50 300 x DN 50 150 | Pressure Limit^{1, 2}(kPa)5102 | Dimensions^{2}
"A" x "B" x "C" (mm ± 1.6) 123.8 x 120.7 x 266.7 | Approximate Weight^{2}(kg) 11.8 |

Inlet and Outlet Code44 | Inlet and Outlet Size DN (mm)DN 50 600 x DN 50 150 | Pressure Limit^{1, 2}(kPa)10204 | Dimensions^{2}
"A" x "B" x "C" (mm ± 1.6) 136.5 x 152.4 x 279.4 | Approximate Weight^{2}(kg) 13.2 |

Inlet and Outlet Code45 | Inlet and Outlet Size DN (mm)DN 50 900 x DN 50 300 | Pressure Limit^{1, 2}(kPa)15306 | Dimensions^{2}
"A" x "B" x "C" (mm ± 1.6) 154.0 x 152.4 x 296.9 | Approximate Weight^{2}(kg) 20.9 |

Inlet and Outlet Code95 | Inlet and Outlet Size DN (mm)DN 50 1500 x DN 50 300 | Pressure Limit^{1, 2}(kPa)16547 | Dimensions^{2}
"A" x "B" x "C" (mm ± 1.6) 154.0 x 152.4 x 296.9 | Approximate Weight^{2}(kg) |

Inlet and Outlet Code46 | Inlet and Outlet Size DN (mm)DN 50 150 x DN 65 150 | Pressure Limit^{1, 2}(kPa)1965 | Dimensions^{2}
"A" x "B" x "C" (mm ± 1.6) 123.8 x 120.7 x 266.7 | Approximate Weight^{2}(kg) |

Inlet and Outlet Code47 | Inlet and Outlet Size DN (mm)DN 50 300 x DN 65 150 | Pressure Limit^{1, 2}(kPa)5102 | Dimensions^{2}
"A" x "B" x "C" (mm ± 1.6) 154.0 x 152.4 x 269.9 | Approximate Weight^{2}(kg) |

Inlet and Outlet Code48 | Inlet and Outlet Size DN (mm)DN 50 600 x DN 65 150 | Pressure Limit^{1, 2}(kPa)10204 | Dimensions^{2}
"A" x "B" x "C" (mm ± 1.6) 136.5 x 152.4 x 279.4 | Approximate Weight^{2}(kg) |

Inlet and Outlet Code49 | Inlet and Outlet Size DN (mm)DN 50 900 x DN 65 300 | Pressure Limit^{1, 2}(kPa)15306 | Dimensions^{2}
"A" x "B" x "C" (mm ± 1.6) 123.8 x 120.7 x 266.7 | Approximate Weight^{2}(kg) |

Inlet and Outlet Code96 | Inlet and Outlet Size DN (mm)DN 50 1500 x DN 65 300 | Pressure Limit^{1, 2}(kPa)16547 | Dimensions^{2}
"A" x "B" x "C" (mm ± 1.6) 154.0 x 152.4 x 269.9 | Approximate Weight^{2}(kg) |

Inlet and Outlet Code51 | Inlet and Outlet Size DN (mm)DN 50 150 x DN 80 150 | Pressure Limit^{1, 2}(kPa)1965 | Dimensions^{2}
"A" x "B" x "C" (mm ± 1.6) 123.8 x 136.5 x 266.7 | Approximate Weight^{2}(kg) 13.6 |

Inlet and Outlet Code52 | Inlet and Outlet Size DN (mm)DN 50 300 x DN 80 150 | Pressure Limit^{1, 2}(kPa)5102 | Dimensions^{2}
"A" x "B" x "C" (mm ± 1.6) 123.8 x 136.5 x 266.7 | Approximate Weight^{2}(kg) 15.0 |

Inlet and Outlet Code53 | Inlet and Outlet Size DN (mm)DN 50 600 x DN 80 150 | Pressure Limit^{1, 2}(kPa)10204 | Dimensions^{2}
"A" x "B" x "C" (mm ± 1.6) 154 x 161.9 x 296.9 | Approximate Weight^{2}(kg) 16.8 |

Inlet and Outlet Code54 | Inlet and Outlet Size DN (mm)DN 50 900 x DN 80 300 | Pressure Limit^{1, 2}(kPa)15306 | Dimensions^{2}
"A" x "B" x "C" (mm ± 1.6) 154 x 161.9 x 296.9 | Approximate Weight^{2}(kg) 25.4 |

Inlet and Outlet Code97 | Inlet and Outlet Size DN (mm)DN 50 1500 x DN 80 300 | Pressure Limit^{1, 2}(kPa)16547 | Dimensions^{2}
"A" x "B" x "C" (mm ± 1.6) 154.0 x 161.9 x 296.9 | Approximate Weight^{2}(kg) |

^{1}Pressure limit may be subject to system conditions and temperatures.

^{2}Pressure limit, weight, and “C” dimension may vary with sour gas service and other options.

^{★}Standard Materials or Options.

^{☆}Flange dimensions compliant with API 526.